RCBOs (known as RCDs)
ESV has imposed additional requirements on the supply of RCBOs (known as RCDs) designed or marketed to be permanently fixed to household or similar electrical wiring in Victoria.
Suppliers must undertake additional testing and verification to ensure their products still operate satisfactorily if there is a defect in the installation or if the product has been installed incorrectly.
These requirements are listed in Additional testing and verification requirements for RCBOs.
Amended prohibition notice
Energy Safe Victoria has amended its prohibition notice on the supply of RCBOs (known as RCDs) to provide more time for industry participants to adjust to the new regime.
In April ESV issued a prohibition notice to halt the supply of certain types of RCDs which testing showed had the potential to fail under certain circumstances. While the likelihood and frequency of such an event was low, ESV took the view that the issue was best addressed by halting the supply of these particular RCDs.
After consultation with industry, ESV has agreed to allow manufacturers a further 12 months to produce new models of RCDs that meet ESV’s strict standards. The revised prohibition notice will come into effect 1 July 2018.
Any products that do not meet these new requirements will be prohibited from sale. Read the prohibition notice – supply of RCBOs.
ESV is currently assessing several models of RCBOs that have been submitted to ESV in response to the prohibition notice. A register of the RCBOs that meet the additional requirements of the prohibition notice will be published 1 May 2018. Suppliers may submit their documentation and products to ESV for assessment at any time.
ESV’s investigation into RCBOs was instigated by a fatality in August 2016 in which it was found that a commonly used RCBO failed to operate.
ESV has identified two situations where 240V can be present on the load side of an RCBO when it is in the open position:
- The device is installed in the opposite orientation to the one indicated by the manufacturer
- The RCBO is installed in the correct orientation, however there is a defect in the installation downstream from the device and there is 240V present on the load terminals when the device is in the ‘off’ position.
If you require further information, please contact ESV’s Equipment Safety team on 03 9203 9700 or at firstname.lastname@example.org.