- High-bay lights are industrial-sized downlights that are used almost exclusively to light up spaces with high ceilings, such as warehouses and factories. The Onsemi products (100 and 120-watt models) in question are LED high-bay lights.
- These are not products usually found in a house.
- ESV has investigated five separate incidents involving 18 lights, 14 of which fell at one particular site.
- Onsemi carried out a recall on its 150-watt high-bay light in 2017 after a number of lights had fallen, based on the weight of the product and the short amount time between installation and failure.
- The lights underwent independent testing and the failure mode could not be replicated under the test conditions.
- Further inspections on the light covers that had dropped showed cracks on the enclosure with sharp edges that had broken off at an angle.
- This suggests that the break was due to external impact/force, and they were not affected by heat.
Onsemi has not sold/manufactured these products since 2019.
- We recommend consumers with these lights installed on their premises to arrange for a qualified tradesperson to check them as soon as possible.
- ESV investigations suggest that some damage to the lights may have occurred during transport or installation, which is consistent with ESV’s engineering assessments.
- This situation does not meet the criteria for a recall based on energy safety legislation.
Date: 22/02/2024 5:15
The currency and accuracy of this document cannot be guaranteed once printed or saved to a storage device. If in doubt, please check the ESV website for the current version.
Reviewed 28 January 2023