Vegetation management workers were pruning a tree on behalf of an electricity distribution business in a low bushfire risk area (LBRA).
The work was being completed as part of a project to transition vegetation from a LBRA clearance standard to a hazardous bushfire risk area (HBRA) standard. The work was being performed by a vegetation management worker operating a Skytrim tree trimmer similar to that pictured below, example pictured.
The Skytrim operator was intending to cut a small branch from the side of a larger branch located at a height estimated to be approximately 13m from ground level. As the operator made the pruning cut the blade extended into another branch.
As a consequence a branch approximately 6m in length was unintentionally cut and fell in an uncontrolled manner onto the adjacent high voltage (HV) conductor. The HV conductor broke at the point of contact and then fell to the ground causing a fire start.
The crew has then initiated their emergency site management procedures. The incident created an unsafe electrical situation that had the potential to cause property damage, serious personal injury or in the worst circumstance an electrocution.
Fortunately, no one was injured. The incident was reported to the electricity distribution business and to Energy Safe Victoria (ESV).
ESV conducted an investigation of this incident and found:
- the Skytrim operator failed to maintain the vegetation Safe Approach Distance (SAD) to uninsulated HV conductors when they pruned the tree
- the crew did not identify and outline control measures to ensure the work could be completed safely.
ESV’s view is that the combination of these failures means the crew members did not comply with the Electricity Safety (General) Regulations 2019, constituting a breach of Electricity Safety legislation; heavy penalties may be applied to such breaches.
- Ensure all site hazards are identified and actions to control the hazards are implemented
- Continually monitor site and environmental conditions and adjust work sequences and practices to adapt to changing conditions
- If necessary, cease work when hazards change and wait until it is safe to continue
- Always maintain appropriate SADs when undertaking works in the vicinity of live electrical apparatus
- Regularly reassess each worksite for hazards when completing electric line clearance work.
- Failing to identify hazards at a work site will place workers at risk of serious personal injury or in the worst circumstance, electrocution
- Ensure each individual work site is assessed for hazards and controls are implemented to manage risks; this should be an ongoing process throughout the work task to adapt to changing conditions
- Working near live high and low voltage electric lines is equally dangerous. A vegetation management worker was electrocuted in February 2019 when they made contact with uninsulated low voltage electric lines.
Having completed its investigation of this incident it is ESV’s view that the minimum clearances from the electric line, as required by the Electricity Safety (General) Regulations 2019, were not maintained. Failing to maintain the minimum clearance is a breach of the regulations.
- ESV’s view is the Skytrim operator failed to ensure the tree he was pruning maintained the required clearance from the electric line, which is a breach of Electricity Safety (General) Regulations
- ESV’s view is the Skytrim operator interfered with protected infrastructure, which is a breach of the Electricity Safety (General) Regulations.
ESV may choose to prosecute or take other enforcement action where it considers a breach of the Electricity Safety Act 1998 or Electricity Safety Regulations has occurred. Heavy penalties may be applied.
For advice and information about line clearance (vegetation management) contact our team in the following ways:
Date: 28/09/2023 20:11
The currency and accuracy of this document cannot be guaranteed once printed or saved to a storage device. If in doubt, please check the ESV website for the current version.
Reviewed 02 February 2023