May 2014There has been a recent serious incident involving a large arc event caused by material falling through an opening in a switchboard enclosure. The switchboard enclosure did not comply with the relevant Australian Standards, in particular AS/NZS 3000:2007 and AS/NZS 3439.1:2002. On investigating this incident, it has become a matter of concern to ESV that there appears to be confusion in the industry as to the IP rating requirements of switchboards and a lack of understanding of the responsibility for compliance. It is also of concern to ESV that the potential for incorrect switchboard design, construction and installation, and subsequent electrical incidents, is not being recognised within the broader industry.
Details of the incidentThe incident involved two electrical workers who were working in a switchboard enclosure, forming part of a large switchboard, fitting a lug to the end of a cable. Lock out, tag out procedures were used and in place. A tinned copper lug fell through a 23mm gap at the rear of the switchboard enclosure. The lug fell onto a live electrical busbar enclosure, which was below the switchboard enclosure being worked on. The lug came into contact with the live busbars causing a short circuit and subsequent arc event, which resulted in extensive switchboard damage. The 23mm gap at the rear of the switchboard enclosure was non-compliant, not obvious and not picked up by the:
- switchboard designer;
- switchboard supplier;
- switchboard builder;
- switchboard installer;
- Registered Electrical Contractor (REC);
- Licensed Electrical Workers (LEW); or
- Licensed Electrical Inspector (LEI).
ComplianceClause 22.214.171.124 of AS/NZS 3000:2007, Wiring Rules –Suitability:
Switchboards shall be suitable to withstand the mechanical, electrical and thermal stresses that are likely to occur in service.
Switchboards complying with the relevant requirements of the AS/NZS 3439 series of standards are considered to meet the requirements of this Clause 2.9.3.Section 7 – Design and Construct of AS/NZS 3439.1:2002 – Low-voltage switchgear and control gear, Assemblies Part 1: Type-tested and partially type tested assemblies (IEC 60439-1:1999 MOD):
Clause 7.7 – Internal separation of ASSEMBLIES
Upon agreement of the form of internal separation between manufacturer and user, verification of internal separation shall be in accordance with 8.2.7.Note: The above relates to the form requirements agreed upon i.e. Form 4A. Section 7 – Design and Construct of AS/NZS 3439.1:2002:
Clause 7.7.1 – By barriers or partitions (standard construction)
One or more of the following conditions can be attained by dividing ASSEMBLIES by means of partitions or barriers (metallic or non-metallic) into separate compartments or enclosed protected spaces
- Protection against contact with hazardous parts belonging to the adjacent functional units. The degree of protection shall be at least IPXXB;
- Protection against the passage of solid foreign bodies from one unit of an ASSEMBLY to an adjacent unit. The degree of protection shall be at least IP2X. Unless otherwise stated by the manufacturer, both conditions shall apply.
Note: The degree of protection IP2X covers the degree of protection IPXXB.The above means that the degree of protection required between compartments or enclosures is IP2X and if IP2X is met then so is IPXXB. AS 60529:2004 – Degrees of protection provided by enclosures (IP Code) states the following in relation to achieving the degrees of protection against contact with hazardous parts and the passage of solid foreign bodies:
- Degrees of Protection against Hazardous Parts (First characteristic numeral 2)
- Protection against access to hazardous parts with a finger. The finger is defined as having a 12 mm diameter and 80 mm length and shall have adequate clearance.
- Degrees of Protection against Solid Foreign Objects (First characteristic numeral 2)
- Protection against solid foreign objects of 12.5 mm diameter and greater. The object probe, a sphere of 12.5 mm diameter, shall not fully penetrate.
Safety outcomeThe two workers involved in this incident were not injured, however this could have resulted in very serious injuries. ESV wants to alert all switchboard manufacturers, suppliers, installers, electrical workers and electrical inspectors to this hazard. The non-compliance of this switchboard was not identified until after the incident had occurred.
The Electricity Safety Act 1998 – Part 3
37) Obligations on registered contractors
A registered electrical contractor must not permit a person to carry out on the contractor's behalf, or direct a person to carry out, any electrical installation work that does not comply with this Act or the regulations.
Penalty: In the case of a natural person, 50 penalty units;
In the case of a body corporate, 250 penalty units.
44) Compliance and testing of electrical installation work
(1) A licensed electrical installation worker must ensure that all electrical installation work carried out by that worker—
(a) complies with this Act and the regulations;
Penalty: 40 penalty units.
45) Inspection of electrical installation work
(4) A licensed electrical inspector must not sign a certificate of inspection of any prescribed electrical installation work unless the certificate—
(a) describes the work; and (b) states that the inspector has inspected the work; and (c) states whether or not the work complies with this Act and the regulations; and (d) contains any other details in relation to the work required by the regulations.
Penalty: 50 penalty units.
The Electricity Safety Act 1998 Part 4- Electrical Equipment
54) Standards of Electrical Equipment
A person must not supply or offer to supply electrical equipment unless-
(a) The equipment complies with the minimum standards prescribed for equipment of that class.
Penalty: In the case of a natural person, 40 penalty units;
In the case of a body corporate, 200 penalty units.As of May 2014, one penalty unit equals approximately $145.00.
Date: 28/09/2023 20:33
The currency and accuracy of this document cannot be guaranteed once printed or saved to a storage device. If in doubt, please check the ESV website for the current version.
Reviewed 15 December 2022